Thread: How many servers in a rack?
12-16-2017, 03:30 AM #1
How many servers in a rack?
Can you tell me how many servers in a rack? What is a Standard Rack Unit and a Server Rack?
12-16-2017, 10:23 AM #2
That depends on the size of the server. But if the size of the server is 1U, a normal full rack can fit 42 servers. (42U)█ RackService.org- Dedicated / VPS / Game Server and Web Hosting
█ Locations: France / Germany / Italy / USA
█Live Chat & Unbeatable Support!
12-18-2017, 11:52 AM #3
A full rack is typically 42u (42 Rack Units).
How many servers you can fit in a rack depends on numerous factors.
A) Server size. We have a couple storage servers that are 4u/server (so you could only fit 10 servers/rack). We also have some that are 8 physical servers in a 3u chassis (which would give you 112 servers/rack) Most servers are 1u/server (so 42/rack).
B) Power - What is the power limit per rack that your data center can support? Servers are no good if you don't have enough amperage to power them.
C) Switch density - Will each server have one network connection, or multiple? How many switches will you need in each rack?
D) Heat - The higher the density, the more heat you are generating in that area. Can your DC support this? Will you need additional cooling?
E) Other equipment - Having 42u of space, does not necessarily mean you have 42u of space for servers. Don't forget about the space taken up by switches, firewalls, KVM, UPS, PDU's, etc.█ █ RDO Servers - Shared Hosting, Resellers, VPS, Dedicated Servers & Clusters
█ █ Windows - Plesk Onyx - Linux - cPanel/LiteSpeed/CloudLinux/MariaDB
█ █ Live Chat - Automated Backups - SSD's
12-19-2017, 06:57 PM #4
Agree with RDO Servers - putting 42 1U servers on a rack may be inviting heat issues - does your data center use cold row containment? Can they adequately cool those servers?ProlimeHost - Dedicated Servers and KVM SSD VPS Services
Three Datacenter Locations: Los Angeles, Denver & Singapore
Cisco Managed Network | Multiple Bandwidth Providers | 24/7 On Site Engineers
12-23-2017, 03:55 PM #5
A standard rack unit (1U) is 1.75" in vertical height, the actual number of units available in a 'full height' rack varies but typically 42U to 45U, or even 47U of empty slots are present - though your provider will likely steal away at least one for the patch panel delivering your connection. Rack mounted servers are designed to fit a certain number of these 'U' such as 1U, 2U, 3U, 4U and so on, which indicates the space they will take once fitted in place (a 1/2U is a short form chassis that can theoretically be mounted 2 per '1U' back-to-back).
Then, we get down to what you can put in, which depends on a few factors including rack depth (e.g. a deep server chassis wont fit a shallow depth rack so check that first), floor strength (as relates to max loading), the Maximum Wattage / Power Density of the DC zone your cabinet will be in (in effect the ability to supply power in, and shift the heat out), and specifically the power supply to your cabinet (usually given in Amps / kVA) and the vertical height of each server (its number of 'U').
It seems broadly accepted (by which I mean recommended) by the main cabinet manufacturers / DC fabricators, etc. not to leave blank spaces between servers (fill them with blanks if they appear), as this interferes with your cooling flow (although you do always hear the odd story that suggests otherwise)... which again is related to the Maximum Wattage of the cabinet... and relates to the HVAC arrangement (CACS/HACS/room-based cooling, etc)... a lot of factors to consider... but as a rule of thumb, nobody should expect to get all their available space filled as one limit or another will be reached... (and yes, there are those that double bank servers at 1/2 U, but thats a whole other story....).
In a well made datacentre, on the balance of probabilities, expect to see your available power supply be the limiting factor though...
01-08-2018, 04:25 PM #6
01-08-2018, 05:42 PM #7
We find that normally with our power usage we realistically fit around 25-30 servers per rack. That way we have flexibility in power and we are not running risk of tripping any breakers. We also noticed a big difference when we moved from HDD's to SSD drives. Our power usage did decrease as well.
01-09-2018, 09:26 AM #8
42 server in 1U rack agreed but you have some issue in this case you may power problem wiring may become complicated and result that it become a lengthy one so just keep in mind all this problem and go with some few you can go with 35 to 36 if you are planning for new
Replies: 6 | Views: 523Last post by CaygriWEB, 01-04-2018, 10:24 AM
Replies: 4 | Views: 438Last post by HostXNow, 12-22-2017, 07:37 PM
Replies: 8 | Views: 468Last post by HostOX, 01-03-2018, 02:40 PM
Replies: 3 | Views: 88Last post by Gladford, 12-31-2017, 08:15 PM
By Lampard in forum Shared Hosting OffersReplies: 0 | Views: 124Last post by Lampard, 12-16-2017, 10:46 PM
Replies: 4 | Views: 463Last post by 24x7serverman, 12-18-2017, 10:48 AM
By SolaDrive in forum VPS Hosting OffersReplies: 0 | Views: 90Last post by SolaDrive, 12-15-2017, 05:44 AM
By HostColor in forum Dedicated Hosting OffersReplies: 0 | Views: 131Last post by HostColor, 12-14-2017, 06:06 PM
By HostColor in forum VPS Hosting OffersReplies: 0 | Views: 114Last post by HostColor, 12-14-2017, 05:52 PM
By mobin in forum Other Hosting OffersReplies: 0 | Views: 110Last post by mobin, 12-14-2017, 02:50 PM
By austenite in forum Shared Hosting OffersReplies: 0 | Views: 3Last post by austenite, Today, 10:56 PM
KVM VPS $9.99/mo 1GB RAM/50GB HD, Linux/Windows OS, Bitcoin/Ethereum/Litecoin/Perfect Money AcceptedBy robert4u in forum VPS Hosting OffersReplies: 0 | Views: 24Last post by robert4u, Yesterday, 06:18 PM
Replies: 2 | Views: 57Last post by Floxera-Jose, Today, 09:25 PM
Replies: 2 | Views: 60Last post by 24x7serverman, Yesterday, 08:54 AM
By Jigz Alvarina Lim in forum Graphic DesignReplies: 0 | Views: 28Last post by Jigz Alvarina Lim, Yesterday, 02:08 AM
By bknights in forum Dedicated ServerReplies: 7 | Views: 2042Last post by VirtuBox, 12-12-2017, 02:47 AM
By HostYouFast in forum Dedicated Hosting OffersReplies: 0 | Views: 215Last post by HostYouFast, 08-09-2017, 03:46 PM
By BlaZeX in forum Dedicated Hosting OffersReplies: 0 | Views: 313Last post by BlaZeX, 06-28-2017, 08:54 PM
OFFER 2x DUAL XEONS/32GB RAM SERVERS FROM 39.99/M! + 50% OFF + HIGH POWERED SERVERS - DUALXEON 24 CORES++By cPanelHosting in forum Dedicated Hosting OffersReplies: 0 | Views: 373Last post by cPanelHosting, 04-30-2017, 05:31 PM
By King-Servers in forum Dedicated Hosting OffersReplies: 0 | Views: 1230Last post by King-Servers, 02-18-2015, 01:29 AM